AP7.2.5. System Requirements
AP220.127.116.11. Independent Equipment: When many alarmed
areas are protected by one monitor station, secure room zones must be
clearly distinguishable from the other zones to facilitate a priority
response. All sensors shall be installed within the protected area.
AP18.104.22.168. Access and/or Secure Switch and PCU: No
capability should exist to allow changing the access status of the IDS from
a location outside the protected area. All PCUs must be located inside the
secure area and should be located near the entrance. Assigned personnel
should initiate all changes in access and secure status. Operation of the
PCU may be restricted by use of a device or procedure that verifies
authorized use. In the secure mode, any unauthorized entry into the space
shall cause an alarm to be transmitted to the monitor station.
AP22.214.171.124. Motion Detection Protection: Secure areas
that reasonably afford access to the container or where classified data is
stored should be protected with motion detection sensors; e.g., ultrasonic
and passive infrared. Use of dual technology is authorized when one
technology transmits an alarm condition independently from the other
technology. A failed detector shall cause an immediate and continuous alarm
AP126.96.36.199. Protection of Perimeter Doors: Each
perimeter door shall be protected by a balanced magnetic switch (BMS) that
meets the standards of UL 634.
AP188.8.131.52. Windows: All readily accessible windows
(within 18 feet of ground level) shall be protected by an IDS, either
independently or by the motion detection sensors in the space.